Most current DSP firmware version: 3B
For the following inverter models:
CSI-50KTL-GS-FLB, CSI-50KTL-GS-B, CSI-60KTL-GS-B, CSI-66KTL-GS-B, CSI-50KTL-GS-FL, CSI-50KTL- GS, CSI-60KTL-GS, CSI-66KTL-GS, Solis-50K-US-SW, Solis-50K-US-SW-F, Solis-60K- US-SW, Solis-66K-US-SW, Solis-50K-US-F, Solis-50K-US, Solis-60K-US, Solis-66K-US
Note: A Solis Update Stick is required in order to perform DSP and HMI firmware updates. Please reach out to your distributor or to Solis US Service to obtain an Update Stick.
Solis inverters have two kinds of firmware: Digital Signal Processor (DSP) and Human-Machine-Interface (HMI)
1. Verify the DSP Firmware Version:
A. Go to Advanced Info > Version > press the Up and Down buttons simultaneously to see "Software Ver". You can also go to Advanced Settings > DSP Update > press enter to see the Current Version
B. If you went to Advanced Info then the DSP version is the two numbers on the left - for example, in the image below the HMI would be version D2
2. Prepare the DSP files for the USB Stick:
A. There are two files that should be on the USB stick: 28335APP and 28335API
B. First reformat your USB stick to FAT32. Then, drag and drop the two DSP files onto your USB stick (make sure they are named correctly)
C. Please note that the 28335APP file will be much larger than the 28335API in case you are unable to tell them apart from each other
D. Ensure no other files or folders are in the USB directory. Right click the drive and click "Eject" then plug the USB stick into the Solis Update Stick.
E. Plug the Solis Update Stick into the green "COM" port on bottom of the inverter
3. Prepare the Inverter and Install Firmware
A. Go to Advanced Setting – Password 0010 - Grid On/Off and turn the Grid to Off. This puts the system into standby mode.
B. Remove the inverter wire box cover
D. Remove the RS-485 Wires that go are used in the communication daisy chain
E. Set the inverter Address to "1" - this is found in Settings
G. Once you insert the update stick, the red and green light will come on the stick. Press and hold the button on the update stick until the lights change to red and amber
H. Go to Advanced Settings > DSP Update > press enter, the current version will be displayed, press enter again
I. Within a few seconds press the button on the update stick and you should see the inverter go directly into update mode.
J. The lights on the stick will fast blink for a minute and then they will slow down. This indicates the update is working. Should the amber light go off after a minute, double check that you have the right update files and that they are named correctly.
K. Once the update completes, the lights on the stick will go solid. Verify that the inverter's DSP version has been updated.
L. Reinstall the RS-485 Lines and turn the grid back on, remove the update stick and screw the black cap back onto the green "COM" port